TEL. : +86-020 31213735 / E-MAIL : firstname.lastname@example.org
We have a team that benefits from over 10 years’ fieldwork and experience
Haoairtech designed this as a portable solution to create a Class 10-100000 clean room environment without the high cost and constraints of a hard wall system.
It’s affordable, reliable, energy efficient and easy to assemble as well as disassemble.
The prefabricated wiring system makes electrical hook-up simple with factory wired components and leg-mounted on/off switches for lights and filters.
A single point electrical hook-up or heavy duty line cord (under 15 amps) are provided, which may eliminate the need for an expensive installation.
Purification Rank : Class10-class 10000
Fan filter unit with mini-pleats HEPA filter/ULPA filter( email@example.com )
Portable Clean room vertical laminar flow booth Control box function :
A: Control the power on/off
B: control the fan filter unit air speed UP/Down
C: Control working area purification light
D: Control the UV light in working area
E: Monitor differential gauge so that replacement HEPA filter in time.
Material : stainless steel 304 or steel with milk color powder coated
pressure Relief valve base one request
Clean room vertical laminar flow booth
Class to class 100.000
According client request
Fan filter unit
Stainless steel, aluminum alloy, AI-Zn plate
Mini-pleats HEPA /ULPA Air filter
Aluminum alloy/stainless steel201/304
Acrylic /sandwich panel/anti-static acrylic
Aluminium –plastic panel , sandwich panel
Constant temperature air conditioning
Or Constant temperature and humidity air conditioning
LED light or T5 (Optional )
Air flow floor
We have a wide range of configuration available to meet most cleanroom booth standards up to Class 10/ISO Class 4.
For Class 10/ISO Class 4 and Class 100/ISO Class 5 cleanliness level,
100% laminar airflow is essential to prevent any deterioration of cleanliness caused by the present of non-laminar airflow.
At this cleanliness level, the ceiling must be totally covered by HEPA/ULPA filter and the lighting is usually tear-drop.
As the result, all particles come from the personnel , processes and equipment are immediately swept away from the clean area.
Where the ceiling is not fully covered, turbulent zones are present. In this cases,
particles introduced or present in the clean area are re-circulated and produce temporary deterioration of the cleanliness level.
Hello, please leave your name and email here before chat online so that we won't miss your message and contact you smoothly.